Skylight Inspection and Certification
An onsite skylight survey and inspection was made on 8/25/2016 by Skylight Specialists, Inc.
Represented by Danny Packard.
Skylights on the site:
- (2) 19’ x 19’ (nominal) structural, acrylic, pyramid skylights. These are in a saw tooth pattern and in a cluster. These skylights are located over the hotel atrium.
- (2) 10’ by 10’ (nominal) structural, acrylic, pyramid skylights. These skylights are located over the pool.
What We Found:
Both the inboard and outboard lights have crazing, cracking and all skylights show signs of condensation.
- Numerous attempted repairs have been made to the skylights, none effective. The “repairs” consist of dumping on tar or mastic, using the wrong sealants, roofing tar, roofing tape ( with large holes in it caused by animals), rubber backer rod to help with gutters and others.